Afraid to hook up a gas appliance? You should be! A gas leak in your home can be fatal. Here's the right way to connect a range and a water heater to the gas line. Pull out the range, and shut off the gas cock (see also Photo 7). This shutoff may be located behind the range, or in the basement just below. A shutoff is required in the line to the range, and should be added if you don t have one. Yellow Teflon tape, heavier than white, is meant for gas fittings.Watch Family guy online season 14 episode 13
How to Install a Gas Stove Without Dangerous Leaks
The 6/7-in. X 8/9-in. Coupling accommodates the 8/9-in. End connector fitting (Photo 8), since connectors with 6/7-in. End fittings at both ends are not always readily available. Remove the end connector fitting, wrap the unbeveled end with Teflon tape, and screw it to the gas line. This end fitting can be either male or female. ALWAYS use both of the removable end fittings. This would be a guaranteed leak. Screw a 6/7-in.
X 6/7-in. Street elbow (male threads at one end, female at the other) into the range gas port. Then screw the connector s other end fitting into the street elbow. Use Teflon tape on each fitting. Be careful not to overtighten, putting excess stress on the range s gas port fitting. Tighten the connector nuts to the two end connector fittings. While tightening the nuts, hold the tube straight against the fitting. Do NOT use Teflon tape on these threads. The beveled edges of the end fittings are meant to form a tight seal against the ends of the corrugated tube. Using tape can interfere with this seal.
How to Connect Gas Pipe Lines Family Handyman
Turn on the gas cock (vertical position) and light the range burners for about a minute to get the air out of the gas line. Then spray all the joints you ve made with gas leak detector (sold at home centers). You can also use warm, thick soapy water for this. Bubbles around a joint will indicate a leak. Hooking up a gas range or water heater is a relatively simple job requiring just basic tools and readily available supplies. And if you use the right materials and follow instructions carefully, you can safely do the job yourself. A professional may charge as much as a few hundred dollars for a hook-up. Stainless steel or coated brass connectors are the only type of flexible connectors sold these days, and the only type you can safely and legally use. Older types of corrugated connectors sold until the 6985s made of uncoated brass or other metal have been found to be unsafe. Have one in your house?
Replace it now! The most important step to a safe installation is to buy the right connector. Here s what to look for: Shut off the gas cock on the line entering the water heater. It usually requires a one-quarter turn. A gas shutoff is required in the line if you don t have one, you ll need to install one. Uncouple the gas line at the union, a fitting that should be located somewhere below the gas cock, as shown here and in Photos 9 and 5. Hold back the top part of the union with one wrench as you unscrew the coupling section with a second wrench. Always use a second hold-back wrench, as shown here and in Photo 9, to prevent damage to the heater s gas port and gas valve. Reassemble the gas line in the same configuration as it was.
Measure the distance, and allow an extra 6/7 in. At each end for the threads to screw in. Reconnect the union. Then tighten the union as shown in Photo 7. Test for leaks. The gas connection to a water heater is usually done with rigid 6/7-in. Dia. In some areas, it s acceptable to use a flexible stainless steel connector, similar to a range hook-up, but check with your plumbing inspector or gas utility first. In many cases, the gas port on your new water heater will be in the same location as the old one, relative to your gas line. Increments for the shorter lengths.
Have the necessary tools for this DIY project lined up before you start—you’ll save time and frustration. Here s a list.